The ACP-DJCS is designed to operate an aerobic treatment unit with a
shaft aerator. This control panel will power one shaft aerator and one
effluent pump. There is no timer to operate the aerator in this control. The
aerator in this system will run continuously. There will be a 360 degree top
mounted red light for alarm conditions and a pizo electric buzzer in the
door of the enclosure.
The 20 Amp pump circuit breaker will supply a 120VAC single phase 1⁄2 HP
or smaller pump. The pump operation is controlled by an Omron H3CRF8
repeat cycle timer. With this timer the pump can be operated from one
second to 30 hours with independent run and rest time settings. This is
helpful when wanting to move small volumes of water like in aerobic drip
fields. The 10 Amp air compressor circuit breaker will power one residential
sized shaft aerator continuously. The 10 Amp alarm circuit breaker will
power the alarm circuit. The High Water alarm is designed to be used with
a normally open float switch. When the high water float switch raises the
red alarm light and buzzer will activate. This control uses a current switch
to monitor aerator operation. The shaft aerators do not have air lines and
rely on a spinning tee on the bottom of the motor shaft to draw air
through the hollow motor shaft and out the tee. If the motor is
disconnected from the power source, shuts off due to thermal overload, or
the circuit breaker trips, the current switch will activate the alarm light and
buzzer. This type of alarm is beneficial over just relying on the circuit
breaker to trip which is found in most alarm systems on the market today.
There are alarm test and buzzer silence switches mounted in the door of
The enclosure has a NEMA rating of 4X which provides protection from
falling dirt, falling liquids, hose directed water and corrosive agents.
The 10”x8”x4” enclosure is made of Polycarbonate and has a hinged
lockable door with latches and included screws to secure the door if
required. All electrical components are mounted inside the enclosure on
an aluminum back plate.
You (the customer) are responsible for making sure you are following all applicable laws and regulations in your area before replacing your septic control panel yourself. Jet is a Registered Trademark of Jet, Inc. Under no circumstances is Wholesale Septic Supply representing to the general public that it is an Authorized Distributor, Dealer, or is affiliated with those companies with whom we make product comparisons or with any products we sell.